- About Us
- Electrical Testing
- Other Services
- Quick Quotes
- News & Blog
- Contact Us
Legislative Updates (Electrical)
BS7671 17th Edition Wiring Regulations 3rd Amendment is now fully current including changes to consumer units (reg 421.1.200) which was delayed until 1st January 2016 to allow time for manufacturers to comply (and presumably to sell off their stocks of plastic consumer boards)
Main Changes Provided within Amendment 3:
UK Specific regulations
There are now some new regulations that are specific to the UK. Any new UK regulation will end in a .200 number.
Definition of Competent
“Competent” person will now be defined as “instructed” person.
RCD’s for all sockets
Regulation 411.3.3 now refers to RCD protection for ALL socket outlets unless
Lower Main Earth Loop Impedance Values
Zs values to take into account the Cmin factor which is for minimum voltage factor. For low voltage supplies Cmin is given as 0.95 which will lower all the permitted values.
Plastic Consumer Units
Regulation 421.1.200 – consumer units, switch boards and assemblies in domestic installations are now to be made of non combustible material such as metal or enclosed in a fire proof boxing or enclosure.
Escape Route Wiring
Wiring in escape routing should be supported and fixed so it’s not liable to collapse in the event of a fire. This would include the use of metal cable ties, metal containment and support fixings which would not fail due to excessive heat.
RCD’s for Cables in Walls
Regulations 522 – Any cable in a wall or partition even commercial or industrial would likely require RCD protection.
RCD’s for Special Locations
Regulation 701.411.3.3 – Cables passing through a special location are to be RCD protected.
Skilled Person Test/Inspection
Part 6 Chapter 61 – Change to skilled person (electrically) being competent in inspection, testing and certification